The Occupational Safety and Health Administration standard on occupational exposure to hazardous chemicals in laboratories (29CFR1910.1450) covers all laboratories engaged in the laboratory use of chemicals. The University's Chemical Hygiene Plan is an "umbrella" document that will cover the major activities conducted at University laboratories. Each laboratory will need to develop procedures and protocols for the unique equipment and chemicals and train those procedures to affected parties. Both the Chemical Hygiene plan and unique laboratory procedures must be accessible to anyone working in the laboratory setting. To request an evaluation of your laboratory for compliance with this standard or for assistance in developing special procedures applicable to your laboratory, please contact Environmental Safety at 6-6485.
Each employee engaged in laboratory work must attend a Laboratory Safety training session which includes the Chemical Hygiene Plan, emergency procedures, waste management and other required topics.
According to Federal and State regulations, all hazardous chemicals used in the laboratory (whether in original or stock containers) must be labeled with:
Any substance that is regulated by a specific OSHA standard must be labeled accordingly by the manufacturer.
Chemical labeling developed and approved by the American National Standards Institute (ANSI) includes a word warning, identification of key hazards, and statements of precautions to avoid the hazard.
Hazard warnings on labels may consist of words, pictures, symbols, or any combination thereof.
Chemicals may also be labeled with the National Fire Protection Association symbol system (NFPA 704). Numbers are used to denote the severity of hazards associated with flammability (red), reactivity (yellow), health (blue) and other special hazards (white) on a color-coded diamond. Higher numbers indicate more severe hazards. Specifically:
0 = no unusual hazard
1 = minor hazard
2 = moderate hazard
3 = severe hazard
4 = extreme hazard
NFPA 45 Table 2-2(a) In sprinkled laboratories, a maximum of 10 gallons of Class I flammable liquids per 100 sq.ft. of laboratory space are allowed outside of an inside flammable liquid storage room. Combinations of Class I, II, and IIIA may not exceed 20 gallons. An additional 10 gallons maximum of Class I flammable liquids may be stored in a flammable liquid cabinet. Combinations of Class I, II, and IIIA may not exceed 40 gallons in a flammable liquid storage cabinet. For help in the interpretation of this guidance, contact EHS at 6-6485 for an on-site evaluation of your laboratory.
NFPA 45 2-1: Anywhere within the laboratory unit. This means it cannot be located in a hallway or any means of egress.
OSHA 29 CFR 1910.106(e)(2)(ii)(b): The quantity of flammable liquid that may be located outside of an inside storage room or storage cabinet in a building or in any one fire area of a building shall not exceed:
When a chemical reaction must remain unattended in a laboratory for an extended period and/or overnight, the researcher must post a sign on the door which is observable from outside the laboratory. The sign describes the nature of the chemical reaction and potential hazards in the event one or more of the utilities for the building fail. The sign must be printed on canary (pale yellow) paper for visibility reasons and consistency with training provided to University Police and Physical Plant staff. The sign may be removed once the reaction is completed or from the time that it will be attended. Click Here for an electronic file of the unattended reaction sign.